I am configuring the FLSTDmSCHE software and I can't get my head round the Valve Command type defined on screens Db10 onward. Could someone shed some light on this?
Here below you will find the meaning of the parameters and the definition of the valve. (Please note that Carel has already received a petition to add in the manual the information below and it will be added as of the next manual version):
D= disable (valve disabled)
O= open (Valve opened)
X= close (valve closed)
I= intermittent (valve intermittent)
P= pulsing (pulsing valve)
N= negative pulsing (negative pulsing valve). This has been inserted as some compressors on the market have this valve always active, while it start pulsing when disabled.
Hope this helps.
Please try to give a substantial answer. If you wanted to comment on the question or answer, just use the commenting tool. Please remember that you can always revise your answers - no need to answer the same question twice. Also, please don't forget to vote - it really helps to select the best questions and answers!